Manual actuation of the relay independent of the bus or switching position indication.
NO contact or NC contact operation.
Central switching function.
Group feedback for reduction of bus load.
Active or passive (object can be read out) cyclical feedback function.
Feedback can be delayed until after the recovery of bus voltage.
Logical linking function for each output.
Block function can be parameterised for each channel. As an alternative, forced setting function for each output.
Time functions (switch-on/off delay, staircase light function – also with advance warning function).
Integration in light scenes is possible, eight internal scenes at the most can be parameterised per channel.
Memory function for light scenes.
Elapsed operating time meter as forward/backward counter with limit function (limit can be changed via bus) can be activated for each output.
Input monitoring for cyclical updating with safety setting.
Reactions in case of bus voltage failure and restoration can be set for each channel following an ETS programming process.
Independent switching of the two outputs.
KNX: Connection and junction terminal
Load: Screw terminals
Contact: 1 x zero-voltage NO contact each, flip-flop
AC 230 V: 16 A / AC1 or 10 A / AC3
AC 400 V: 10 A / AC1 or 6 A / AC3
DC: 16 A/24 V
Maximum switch-on current: 400 A, 150 µs, 200 A, 600 µs
Ohmic load: 3600 W
Capacitive load AC 230 V: 16 A, max. 140 µF
Light bulbs: 2500 W
HV halogen lamps: 2500 W
Wound transformer: 1200 VA
Gira Tronic transformer: 1500 W
Fluorescent lamps, uncompensated: 2500 VA
Fluorescent lamps, duo-circuit: 2300 VA
Fluorescent lamps, parallel-compensated: 1300 VA
Mercury-vapour lamps, uncompensated: 2000 W
Mercury-vapour lamps, parallel-compensated: 2000 W
Connections: max. 4 mm²